Which are the steps of the socket welding? The socket welding, also known as polyfusion or fusion welding, is used to join a pipe with a fitting from 20 up to 110 millimetres (mm) of diameter. Knowing which the steps of the socket welding is essential to do very well the join between the pipes and fittings that can be of polyethylene (PE), polypropylene (PP), polybutadiene (PB) and Polyvinylidene fluoride (PVDF). In brief, we will say that the socket welding is done by introducing the pipe within the fitting when both reach the temperature enough like to fuse the material. In the case of the pipe, the part which gets hot is the external past, while in the fitting it is the internal part. Both components must be done of the same plastic material. Which process is followed in this type of welding? 1. Cut both ends of the pipe and, after cleaning them, bevel them to let the fitting enter easily. A good reference for the bevelling is 1.5 mm from the external edge exterior of the pipe. 2. Check that the depth of the insertion is correct for the pipe by means of a measure. Align the cold ring with the end of the pipe to round the pipe before removing the measure. 3. Confirm that it has been achieved the necessary fusion that we will know because we will have proved the thermo characteristics of the material before beginning the welding. We will have to wait some minutes up to the moulds also achieve the temperature. 4. Make sure that both the pipe to be welded like the internal side of the connection or fitting are clean. …………….. 5. Start the join. The thermic element should be placed perpendicularly to the connection and to the pipe, which will be joined at a time. The connection is placed over the male mould and the pipe over the female mould. With precaution not to turn the moulds or the materials, the thermic element must butt against the end. Once it is got, it is kept until the heating time of the welding ends 6. Remove the elements of the moulds once it is fulfilled the heating time. It is important to do it with precaution not to turn them during or after the join. Then, they are joined up to the fitting makes contact with the cold ring. 7. Put some constant pressure up to the necessary cooling time is fulfilled. Once this point is reached, let it ‘rest’ during around ten minutes (always following the times indicated by the normative). To make sure that there are no problems at the moment of fitting together and welding, it is important to take into account that the fittings and connections to use for this join they must have a wall thickness which surpass the percentage of the thickness of the pipe which we want to introduce in the internal side of it. Post Relations: The handling and assembly of PE pipes Multilayers pipes, what are they and what are they used to? The use of plastic pipes in the networks of fire protection systems By nuevoaristegui|2017-05-07T13:40:25+00:00November 16th, 2015|Recent news, Thermofusion pipe welding|0 Comments Share if you liked! FacebookTwitterLinkedInGoogle+Email Related Posts Leer articulo Why the hot air welding is the most indicated to repair a tauliner? Why the hot air welding is the most indicated to repair a tauliner? Leer articulo The use of PVC pipes for wastewatertreatment The use of PVC pipes for wastewatertreatment Leer articulo Benefits of the use of TPO roofs for waterproofing Benefits of the use of TPO roofs for waterproofing Leer articulo Six advantages of plastic pipes in sanitation applications Six advantages of plastic pipes in sanitation applications Leer articulo What should I take into account to at the moment of buying a hot air welder? What should I take into account to at the moment of buying a hot air welder? Leer articulo Some advice for the reparation of deposits by filler rod Some advice for the reparation of deposits by filler rod Leave A Comment Cancel reply Comment Save my name, email, and website in this browser for the next time I comment.